Technician was most pleasant. He performed the service on both of my units with professionalism and was extremely neat.WoodstockGA30188 34.0775-84.44
I was very pleased with the installation of new ducting to supply a newly enclosed sunroom. Chris was his usual great worker and completed the job to my satisfaction.WoodstockGA30188 34.0775-84.44
Professional and courteous. 5 star service!WoodstockGA30188 34.0925-84.5125
Dennis is the Best! But I have to say that all techs are very good. always on time, knowledgable, and professionalWoodstockGA30188 34.1025-84.51
Elbow for flue pipe in attic broken. Will need to replace dura-vent 4” double wall elbow. Pic uploaded
2 system PM renewal Upstairs- checked heating operations of system. Replaced filter, checked capacitor output and amp drawls, cleaned flame sensor and burners, triggered safety switches. Unit is operating properly at this time. 16x25x4 Main- checked heating operations of system- changed filter, checked capacitor output and amp drawls, checked Freon levels and auxiliary heat, triggered safety switches and defrost. Unit is operating properly at this time. 16x25x4. Customer provides filters
Furnace- Checked heating operations of system. Replaced filter, checked capacitor output and amp drawl, trigger safety switches, cleaned flame sensor, cleaned burners, and cleared drain line. system is operating properly at this time. Heatpump -Checked operations of systems. Replaced filters, check capacitor outputs and amp drawls, checked refrigerant levels and auxiliary heat, triggered safety switches and defrost modes, and cleared drain lines. Systems are operating properly at this time 16x20x1. 2-16x25x1.
Install new 120v 10” in-line ventilation fan
Ventilation fan has bad bearings causing it to be noisy. Will need to replace. Estimate has been sent and approved.
Performed maintenance on furnace filter do not need to be changed homeowner said she changed it recently cleaned off flame sensor checked all electrical components for broken or loose connections checked capacitor checked amperage on fan motor everything is running normal at this time
No one home rescheduled
Upon arrival customer stated that he is waking up to temperatures lower than he initially set the night before. Previous technician believed it was the thermostat since it was so intermittent. I found that the furnace shortly after firing up would throw a fault of high limit switch open. These trane furnaces run the pressure switch, roll outs, and high limit into one plug. As i have seen on these older trane furnaces, these 12 pin plugs wear out. I was able to confirm this by wiggling the wiring harness, system would then either go out on high limit again or quickly stop the gas valve signal and start up again. Less than a second. I replaced trane board with a residio universal furnace control board. Furnace is heating home properly at this time.
Performed 2 system heating maintenance. Checked both filters are they are both in good condition. Customer will have replacement filters for next visit if needed. Both systems clean and operating properly.
Performed 2 system heating maintenance. Both 16x25x5 media filters still in good condition. Both systems clean and operating properly.