The service that has been provided to us has always been exceptional!
Performed 1 system heating maintenance and replaced air filter.
Evaporator coil has been swapped. System is currently functioning properly with no leaks.
Lowered fan speed to t1
Main level Unit is not cooling properly because the indoor coil has a leak. Have to order coil Monday morning from apex lithia springs
Compressor amps were very high due to dirty condenser coil. Technician cleaned condenser coil and head pressure And amperage dropped exponentially. Customer says system is cooling fine. Technician checked filter, will need to be changed on next visit. Ductwork in ventilated crawlspace was sweating profusely. Homeowner may want to invest in a dehumidifier. System refrigerant charge is good. Capacitor, contactor, fan, blower, and compressor all running proper amperage and microfarads. System functioning properly at this time. Customer mentioned odor is coming from system. Technician sent an estimate for a photo max UV light.
Checked for dye and found none at this time told him to call us if it stops cooling again and then we would be able to find it then. Asked about billing and he said we are suppose to bill his son at apex and they will settle it up later.