Checked water leaking from vent and found nothing wet when I arrived. I sealed the gap between the boot and ceiling with silicone and installed the grill back on the ceiling, also checked pressures and added a pound of Freon. Spoke with owners about extending maintenance in July as it will be a year they have moved in and he said to have office contact him to set it up.
System has been started however it does need the ductwork to be completed and the zoning to be completed may require a zone panel and wiring along with ductwork. Will need to provide an estimate. Office will schedule ductwork design engineer to come and provide estimate. Inspected refrigerant level and unit is cooling.
Replaced compressor in Whitesburg Ga
Service call completed in Whitesburg Georgia.
Replaced compressor, and refilled system in Whitesburg Ga
Replaced compressor, replaced TXV, and by flow filter dryer. Refilled system with 410 a refrigerant. System is operating properly at this time. Warranty.
At first we operated unit in cooling mode and cooling mode the compressor sounded not good and we are not getting any refrigerant back to our condenser. Operated unit in heating mode and compressor not pumping refrigerant. Will need to replace compressor, TXV, and liquid line bi-flow dryer. Office will schedule return visit for repairs once the parts have arrived. New construction warranty
Technician performed one full system maintenance which includes indoor air as well as outside heat pump. Technician checked all electrical components for amp draw, mfd, and all high and low voltage connections. Technician checked blower wheel as well as blew drain line out of all algae and debris. Technician checked charge on out door heat pump refrigeration and cleaned condensing coils. Armor flex on line set was made sure to be insulated . Over all status of air conditioning is in manufacturing specifications. filter was changed and dated for customer.