Completed two system ccm maintenance I checked thermostat operations treated drain line and condesate pump. I also added pvc union for upstairs so it can easily be cleared or treated in future . I changed both filters, customer provided 20x20x5 filter. Checked electrical connections and components, checked overall cleanliness of systems and blowers checked capacitor mfd outside fan motor amps and Freon levels, also performed condenser wash and cleared debris from condensers, both systems operating normally at this time, units are all pretty new except basement air handler informed customer he opted to wait until it starts acting up.
Completed single system cooling maintenance. Replaced 30 x 20 x 1 filter. Homeowner provided. Cleared and treated drain line and condensation pump, checked electrical components and indoor unit. Checked electrical components and outdoor unit, clean coils and check charge system is currently cooling at manufacturer specifications. .
I cut the bathroom vent in tied it in also moved the vent in the kitchen to the other side of the wall. I also moved the return in the bedroom fort was no longer underneath the cabinet. I also ran what was left in the basement for flex, I cut the hole for the hood vent but we will need to return with two elbows to tie it in open the attic
Didn’t have the right Materials to do job
Cut in the toe kick
Checked thermostat operations and turned it to emergency heat. Checked heat kit amps. Checked the zoning system. Checked the blower amps. Checked the overall cleanliness of the system and the blower. Went outside and checked the compactor MFD. Checked the fan motor amps. Checked freon in regular heating mode. Filter was good, customer had just changed filter. System is operating normally at this time.
I Cut in all the grills for the basement the u/s floor is still wet could not do the toe kick. I ran the supply to the garage and connected it with the toe kick stock wall
I performed a heating maintenance on two heat pump air handler units I replaced two 14x20x1 filters and one 16x20x5 I checked all electrical components and checked the temp rises and checked the Freon levels and checked the capacitors everything is in good working order at this time.
Adding a supply run and connecting a existing supply run. Reduced cost of original quote due to materials provided by customer.