you're asking me to give you feedback on Christian Rice, he did not perform the work. O my God do you even know who you sent here?
Good service plan
On time, professional, answered questions, seemed very knowledgeable
Came out same day to give an estimate for a whole new system. No pressure to buy or up sale on more expensive systems. Helped keep house cool until new system could be installed. Patrick went above and beyond to make sure my family stayed cool without breaking the bank. Crew came out as soon as possible, worked very efficiently. Got finished with everything before the house had time to get hot again. I would highly recommend Comfort Solutions to everyone I know.
Jason handled a new HVAC system in a new home I built. We had several conversations regarding my options, his recommendations and pricing. I also contacted at least 3 other local HVAC contractors. For the quality of the equipment, Comfort Solutions was the clear choice. Comfort Solutions then exceeded my expectations with the actual installation. Great Work!
The tech they sent to look at our HVAC arrived on time, was genuinely friendly, and explained everything well.
Technician performed one full system heating maintenance which includes indoor air handler. Technician checked all electrical components for amp draw, mfd, and all high and low voltage connections. Technician checked blower wheel and heat strips. All pressure and safety switches were checked and tested. Filter was changed and dated for home owner. Over all condition of air handler and heat pump is in manufacturing specifications and safety codes. Heat pump coils were cleaned and charge checked.
Installed 4" wall cap
Installed 16 inch collar on supply plenum, duct work is functioning properly.
Technician performed one full system heating maintenance which includes indoor furnace. Technician checked all electrical components for amp draw, mfd, and all high and low voltage connections. Technician checked blower wheel and exhaust fan. All pressure and safety switches were checked and tested. Filter was changed and dated for home owner. Technician removed and cleaned burner track and sanded ignition stick. Heat exchangers were surveyed and no cracks were found. Over all condition of furnace is in manufacturing specifications and safety codes. Replaced armor flex on entire line set inside.
Performed heating maintenance for a full hvac system, including indoor furnace. Checked all electrical components for amp draw, mfd, and all high and low voltage connections. Inspected blower wheel and exhaust fan. All pressure and safety switches were checked and tested. Filter was changed and dated for home owner. Removed and cleaned burner track and sanded ignition stick. Heat exchanges were surveyed and no cracks were found. Overall condition of furnace is within manufacturing specifications and safety codes. Heat pump coils were cleaned and a/c charge checked.
Replace both blower and dual capacitor for the upstairs system
Upstairs System Apparently has had a small leak at some time. We topped it off in the spring and worked fine all summer according to the customer. 16x25x1 Filter needed to be changed. Blower housing very dusty. The heat sequence started properly after technician cleaned the flame sensor. The burners are slightly warped due to the gas valve stub out not being supported causing some erratic rollback on flame burners. Technician helped it out a little bit but it will need to be supported to avoid future rollout issues. (Picture attached) Technician noticed blower was running high amperage, factory specifications calls for 5.6 amps Max, system was running at 5.7. 10uf single capacitor had a 7.6uf draw. Low capacitor microfarads combined with dirty blower wheel (picture attached) is what is causing such high stress and amperage to blower motor. Will become a problem in future if repairs arenâ€™t made. Upflow Drain Pan in attic doesnâ€™t have an overflow shutoff switch. For a system that
Checked operations the door was not on properly so I put it back on and everything starting working. Homeowner said he took it off bc it was not working. Let the system run to checked pressures and Freon was fine, could not find any issues at this time.
Customer just wanted a quote on replacement. Estimate has been emailed to customer
1 system ccm- Checked heating operations of system. Replaced filter, checked capacitor output and amp drawl, trigger safety switches, cleaned flame sensor, cleaned burners, and cleared drain line. system is operating properly at this time. 16x20x1 Blower capacitor is not within range itâ€™s a 7.5 and reading a 5. Customer decided to replace it and unit is now working properly Also made customer aware about units age but customer wants to wait a little longer To change it out and once that time comes we will reimburse the blower capacitor