Tech even showed up early which was appreciated. Respectful and friendly. Knew his business.
Technician performed one full system heating maintenance which includes indoor furnace. Technician checked all electrical components for amp draw, mfd, and all high and low voltage connections. Technician checked blower wheel and exhaust fan. All pressure and safety switches were checked and tested. Filter was changed and dated for home owner. Technician removed and cleaned burner track and sanded ignition stick. Heat exchangers were surveyed and no cracks were found. Over all condition of furnace is in manufacturing specifications and safety codes.
Changed 2-16x25x2 filters. Part of maintenance visit thatâ€™s already paid for
Fuse blown. Replaced fuse and system operated properly. Checked all zones to make sure they worked properly. System is operating and dropping temperature. Not sure why fuse blew
Checked operations the drain was clogged cleared the drain system can now drain properly.