Friendly service with a smile. The job got done without a hitch.SnellvilleGA30039 33.8325-84.04
Performed system maintenance. Replaced 1-20x20x1 & 4–16x16x2 filter.checked blower belt wear and tightness. Checked app draw on the system and checked all electrical components. Cycled system to confirm correct function at the thermostat. System is currently operating at manufacturer specification.
Completed CCM form for 2 systems Main level system is now heating 90+ efficiency furnace condensate tubing had frozen. Now with warmer temperatures line have the thawed pump emptied itself and system is operating. Customer interested in maintenance contract for 2 systems. Downstairs filter size is 18 x 25 x 4 or 1 inch can be used. Upstairs filter size is 20 x 25 x 1. Performed heating maintenance on both the downstairs and upstairs furnace is including cleaning flame sensors inspecting filters inspecting electrical connections and components. Testing heat exchangers. Cleaning tubing on pressure switches. And treating condensate drain areas. The upstairs furnace is a 80% furnace and does not make water while heating. Both systems are operating properly at this time.
Performed 1 heat pump package unit maintenance and replaced 4-16x16x2 filters. System clean and operating properly.
Maintenance/tune up completed in Snellville Ga
I performed a cooling maintenance on a single rooftop unit I replaced four 16x16x2 filters I checked all electrical components and checked the Freon levels and checked the capacitors everything is in good working order at this time.
Replacing furnace control board
Checking a power issue on 2 systems.