Performed 2 system cooling Pm replaced 16x25x1 filters. Checked electrical components as well as refrigerant charge all systems operating optimally at this time
Checked system operation, system operating properly. Did have to seal up system between furnace and evaporator coil with silicone. Warranty
Chris was able to give this customer a free in home quote for a new system. he provided financing options as well. Chris also provided an estimate to move the furnace to the attic.
The current location of the 19 year old natural gas furnace is against code. It currently doesn’t have adequate combustible air. Which will cause excessive CO to inter the home. Due to location and age of system it is highly recommended to relocate and replace
Performed maintenance on two furnaces changed out to 16 x 25 by one filters cleaned flame sensors checked capacitors checked amperage on fan motors everything is running normal at this time
Residential service call completed in Scottdale Ga
Maintenance/Tune Up completed in Scottsdale Ga
Replaced warranty T6 thermostat
Performed inspection on two furnaces inside attic, treated the drain line and change to 16 x 25 x 1 filters, checked all electrical components on furnaces. Performed inspection on outdoor condensing units, checked refrigerant and all electrical components, The system is clean and performing as it should at this time.
Quoted pricing on a new system.