Thanks for installing the downdraft duct and gas line. We will be calling you again.
Technician out here on august 21 misdiagnosed the issue. The blower wasnâ€™t spinning due to the blower communication wire was in the wrong terminal on the basement thermostat.
Replaced duel capacitor Customer is interested with system replacement. He applied to finance system and application is currently under review. Once approved we will move forward with replacement
Checked operations system still needed Freon after changing txv. Pressures were bouncing around a little I was able to get them to stabilize and be consistent after adding more Freon to the system. The system Seems to be running normal operations at this time.