Thanks for installing the downdraft duct and gas line. We will be calling you again.
I performed a cooling maintenance on two gas furnaces I replaced both 16x25x1 filters I checked all electrical components and checked the temp drop and cleaned both drain lines and I checked the Freon levels and checked the capacitors everything is in good working order at this time.
I performed a cooling maintenance on two gas furnaces and Ac units I replaced one 16x25x1 filter in the upstairs unit and I replaced the 16x25x5 filter for the downstairs unit I checked all electrical components and checked and cleaned the drain lines on both units I checked the temp drops on both units but I found on the downstairs unit the temp drop was not good and I checked the Freon levels and checked the capacitors I found on the downstairs Ac unit that it was a little low on Freon so I added a Lb of Freon to get it to the right levels everything is in good working order at this time.
Replaced bad defrost control board for 2 ton system. Checked operation and system operating properly.
Replaced condenser fan motor for Diakin rooftop package unit.
System not coming on service call completed in Roswell Ga
Found in memory care units to be in operable units are no longer connected to chiller which has been removed from building Recommendation is installing minisplits in each corner of the room
Commercial Quote completed in Roswell Ga
Found main unit float switch open circuit causing the 24 V circuit to be open. This will not allow the system to operate. Customer approved at this time to replace the float switch. I replaced the float switch and observed normal operation from the system after repair. For the office space system, I found the defrost control board for the outdoor unit was not providing common to the contactor. I found 24 V for the yellow wire which indicates that the air handler is calling to cool. I found no continuity from the common wire at the Contactor to the common wire going into the control board from the air handler. The customer has approved replacement of the defrost control board at this time. The part is under warranty however the labor is not. I have ordered the control board from the supply house. We will be reaching out to the customer to schedule the appointment to replace the control board. The estimate has been sold for later job.
Maintenance/tune up completed in Roswell Ga
I performed a cooling maintenance on five rooftop units I replaced six 16x25x2 filters on three units, two units I did not replace because one unit is not working the compressor is dead and the disconnect box needs to be replaced and dew to the age of it and it is a R22 unit it needs to be replaced the other unit it is working but the fan motor is dead and it needs to be replaced and on that one it has a different size filters they are 16x20x2 and there is four, the other three units are in good working order at this time but they are being over worked because of the other two units that are not working. On the unit that needs a fan motor I did replace two fuses that go in the disconnect box.