Thanks for installing the downdraft duct and gas line. We will be calling you again.RoswellGA30076 34.0175-84.285
Performed maintenance on furnace in the crawlspace changed 20x25x5 filter cleaned off flame sensor checked all electrical components for broken or loose connections checked capacitor checked amperage for fan motor everything is running normal at this time
Remove heat pump Install new 4 ton gas pack with new adapter curb Install half-inch regulator Connect back into existing gas line Reconfigure thermostat for gas from heat pump
I performed a heating maintenance on two gas furnaces Ac units I replaced both 16x25x1 filters I checked all electrical components and checked the temp rises and checked the heat exchangers and checked the gas pressures and checked and cleaned the flame sensors everything on both unit are in good working order at this time.
Operating pressures today were 98/227 with 6° sub cooling. Temperatures on either side filter dryer pretty close to being the same around 71°. Office will Schedule return visit with 2 technicians and additional time. top of unit will have to be removed, And four or 6 foot ladder need to access txv location.
Vents to baby room and spare room were closed, the one in the baby bedroom had furniture blocking vent as well. Moved furniture about 4 inches off the wall to allow for vent to blow. Opened babies room vent all the way and partially opened one in spare bedroom. Told customer to try and see if that helps the issue, if not we will add more dampers.
Performed inspection and maintenance on one crawlspace and one attic furnace unit. Changed both filters and treated drain lines and condensation pumps. Inspected capacitors, pressure switch tubes and orifices. Inspected flame sensors and igniters. Performed functionality check on both units. Checked blower and exhaust fan amperages. Checked burners. Checked for leaks in supply. Checked for leaks in flue pipes. All measurements taken are within specifications. Both units are functioning normally at this time. Customer has opted to sign up for the monthly membership program at this time. One of the returns came off for the middle live for the upstairs system that was part of the reason why the system was not working properly.
I performed a maintenance on 5 rooftop system the shutoff vale was turned off on every one of them turned them on . Then I tested all the low voltage on them checked the belts and also changed the filters they are running and operating like they should be.
Replace the front plate of the T6 thermostat charge them for labor on the thermostat only
Completed one ccm maintenance on gas furnace i inspected gas and exhaust i did not change filter homeowner did before i arrived fresh one was left with customer, i pulled and cleaned flame sensor, I cleared pressure tube i inspected overall cleanliness of cabinets and blower as well as burners and inside heat exchangers i watched unit cycle got inducer and blower amps, system performing as it should at this time.
Customer says thermostats cuts on and off randomly mostly at night time recommended maybe swapping out old thermostat for a new one but she wants to give it more thought