Thanks for installing the downdraft duct and gas line. We will be calling you again.
Upstairs system is working properly. Filter is clean, blower is operating, system is draining, coils are clean, and refrigerant levels are in range. Customer is aware about the systems age but is not interested in replacement until next year. Pic uploaded
The main level is low it is a r22 system wants the price on changing the system out soon as possible
The compressor is bad need to change out system or do a ac coil change out the homeowner wound a good deal
Changed out capacitor on the system and still did not coming on tested the wires and I was getting 24 volts. The wires were good tested the fan motor and that was good thermostat was not good. homeowner had one here at the house that was new put it on and the system started to cool
Changed out compressor
Indoor blower motor for downstairs basement system capacitor needs to be replaced need to come back with a 7.5 MFD did not have any on van
Maintenance/Tune Up completed in Roswell Ga
Maintenance/Tune Up complete in Roswell Ga
Performed inspection on two furnaces one in the walk-in attic and one in the crawlspace, checked blower amps and capacitors and the upstairs capacitor is in the process of going bad also changed 16 x 25 x 1 filter and 14 x 20 x 1 filter and blue drain lines out, performed inspection on outdoor condensing units, found bad capacitor on main level condensing unit, I replaced the 40/5 capacitor and checked refrigerant levels and all other electrical components, both systems are now clean and operating normally at this time. Old capacitor is reading 33.20
Performed inspection on two furnaces and one air handler, blew out all drain lines and treated them also, only changed 16 x 25 x 1 and upstairs furnace, checked blower amps and capacitors, perform temperature rise on all three systems, performed inspection on outdoor condensing units and heat pumps, checked electrical components and refrigerant levels, all three systems are clean and operating normally at this time.