Dennis did an awesome job fixing an oops by the main installation crew. I will recommend Comfort Solutions in the future.
I performed a maintenance on a single heat pump air handler I replaced the 16x20x1 filter I checked both heating and cooling both are in good working order I replaced the thermostat and took pictures.
I performed a cooling maintenance on a package unit I replaced the 20x25x1 filter I checked all electrical components and checked the Freon levels everything is in good working order at this time.
I have already taken all the pictures of everything and there is still no power to the house I checked the electrical panel and turned on all the breakers and still no power to the house so I can not perform a maintenance on this unit at this time.
Install new system in Rockmart Ga
Performed inspection and maintenance on one indoor heat pump unit, and one outdoor condensing unit. The system will not turn on cool mode. When cool mode is selected, the system operates under heat mode. When heat mode is selected, the system does not produce cooler but The blower fan circulates ambient temperature air. This is due to the thermostat not being capable of running the system. It is a conventional furnace/AC thermostat. Changed filter, treated drain line and condensation pump. Inspected lower amperage, blower capacitor which measures below specifications, and overall cleanliness of the blower compartment which is very dirty. Inspected evaporator coil and attached photo where the evaporator coal fins or mashed down causing poor airflow through the evaporator coil. Inspected outdoor condensing fan motor amperage, capacitor, and Freon level. Washed outdoor condensing unit coil. Due to the age of the system, the evaporator coil needing to be replaced, the thermostat needing to
Performed maintenance in Rockmart Georgia.
Inspected systems in Rockmart Georgia.
Performed start up of system- Rockmart Georgia
Performed startup of system. Connected orange wire at splice in attic. All colors are now connected. Pulled deep vacuum, opened king valves, and set refrigerant charge. System is operating properly. Filter size is 18x20x1.
Estimate to add ductwork for downstairs