Dennis did an awesome job fixing an oops by the main installation crew. I will recommend Comfort Solutions in the future.
Warranty- system had 2 filters installed, one in return upstairs and in system. I removed one in system so 20x20x1 filter at return is only needed. I also added a p-trap. System is working properly with Freon levels in range. Pics uploaded
The pvc at the condensation line was not glued so I glued the pvc checked the charged system is operating and cooling the house
Installed new 35/5 mfd dual capacitor and filled system with 2 lbs of R410a refrigerant.
On arrival found both units not working. The fuse in the air handler was blown because the compressor wire half and shorted it out. I Strip of wires wiring nut on it Compressor came home and started working check charge and it is good
The tab on the condensation pump was not pulled. I pulled the tab and the pump came on and drained all the Walter out system came on everything is working
Residential Service Call completed in Rockmart Ga
Warranty- replaced indoor coil and system is now cooling properly. 14x20x1 Pics uploaded
Found bad indoor evap coil.
I performed a maintenance on a single heat pump air handler I replaced the 16x20x1 filter I checked both heating and cooling both are in good working order I replaced the thermostat and took pictures.
I performed a cooling maintenance on a package unit I replaced the 20x25x1 filter I checked all electrical components and checked the Freon levels everything is in good working order at this time.