Warranty- At some point this house was zoned and supply dampers were not removed. Downstairs damper was getting stuck closed and not cool area. I removed damper and system is now working properly. 20x20x1, pics uploaded
Removed 3-24”x24” lying nd installed 2-10x6 and 1-14x6 boot and connected ductwork
Customer has had Sheetrock ceiling put in but none of the ducts were strapped to ceiling so they fell when drop tile ceiling was removed. Customer was charged for the Sheetrock company having to hang them. Told customer we could’ve installed different boots for the Sheetrock ceiling but the Sheetrock company is coming back today to finish the ceiling, so we can’t get it done before they arrive.
Completed- I replaced the indoor txv ,pressure tested the system and pulled a deep vacuum. I started the system up and adjusted the charge to factory requirements. System is currently cooling, temperature in the house is high and it will take a while to bring the temperature down to the set temperature.
I performed a maintenance on a heat pump in the attic filter is 20 x 25 x 1 was already changed I Look at the blower motor and check the capacitor and blew out the drain. I’ll check the charge on the outdoor unit and the capacitor and wash the system off. The system is running on operating like it supposed to.
The in indoor Txv is bad and backing the system down and shutting it off in low pressure lock out we’ll need to return and change out
2014 Lennox heat pump low on refrigerant. Tried to call and text Selena for 30+ minutes and no answer. Will be sending quotes to her email for refrigerant and a electronic leak search to pinpoint leak. Pics uploaded
I performed a one system maintenance on a heatpump in the attic. I look at all the low voltage and blower motor and treated the drain line and checked the compaster. I checked the charge and compaster on the out door system and washed the out door system as well filter size is 20x20x1
I performed a one system maintenance on a heat pump in the attic. I looked over the low-voltage check the capacitor check the blower motor and treated the drain line. Check charge and the capacitor on the outdoor unit and I also washed the outdoor system off. System is performing at operating like it should be. The filter for this one is 20x25x1
ZERO percent financing for 36 months. WAC