Timely, knowledgeable, and professional technician
The service I received was great. I got a quote on the service I needed and the service person arrived on time and was efficient in checking for problems.
Came on time and although it was a cool day, did a thorough job at finding what the issue is. Very professional and clean!
The technician was kind, thoughtful, and thorough. He explained everything well and did not push extra services, except to mention and explain other options. He arrived on time. It was easy to schedule an appointment with their office that was convenient with me. I would highly recommend Comfort Solutions.
Dennis came by to diagnose an issue with our unit. He was courteous, knowledgeable and the pricing was fair.
Tech was on time fir appointment and very polite. Will use again
Quote on all new hvac
Performed heating maintenance on two furnaces one in the attic one in the basement, did not change 16 x 25 x 5 filter in downstairs but did change 16 x 25 x 1 and upstairs system, cleared both train lines and checked blower motor amps and all electrical connections and components, triggered safety switches, cleaned burners and sensors, checked pressure tubing and switches, both systems are heating normally at this time.
Performed Heating maintenance on two furnaces and two air handler’s, chaned 16 x 25 x 1 and 16 x 20 by one filters and two furnaces in upstairs area, cleaned burners and flame sensors, checked the blower motor amps and temperature rise, checked all electrical components and connections on furnaces, also treated drain lines on furnaces, changed 20 x 20 by one filter in ceiling grill and 16 x 20 by one filter at system, checked blower motor amps and temperature rise on both air handler‘s in right side of building, cleared drain lines and checked all electrical connections, changed 20 x 20 by one filter in rental building on the left side of building, could not check heating due to no gas line ran, performed inspection on two heat pumps on the side and behind the building, checked refrigerant levels and all electrical components and connections. All five systems are clean and operating normally at this time.
Performed heating maintenance on one Trane furnace inside basement, checked capacitor MF diesel and amp draws of blower motor, triggered safety switches and treated drain line, changed 16 x 25 by one filter, cleaned flame sensor and burners, blew out pressure tube, checked exhaust fan amps, the system is heating properly at this time.
I performed a heating maintenance on a single gas furnace Ac heat pump dual fuel I checked all electrical components and checked the temp rise the heat pump came on and the gas furnace the burners good and checked the flame sensor and I cleaned the outside unit everything is in good working order at this time. I did not replace the filter homeowner has already replaced the filter.
Quote on all new hvac
Upstairs 2000 Ruud AC not working properly because unit is low on refrigerant and AC coils also dirty. Due to age and system contains the phased out R-22 customer is interested in see a comfort advisor ASAP Pics uploaded Reimburse diagnostic fee with repairs or replacement
Warranty- replaced shorted damper for the main level and cleared drain. System is now cooling properly. Pics uploaded
Warranty less than one year. Compressor windings are shorted internally. Compressor will need to be replaced. Airhandler condensate is substantial. Ductwork also condensating. No filter in system? At this time with compressor not operational unable to determine what refrigerant charge was like prior to failure.
Maintenance/Tune Up completed in Powder Springs Ga