2020 Rheem heat pump is working properly. Customer did mention that he almost called to cancel service call because once he replaced the dirty 20x25x1 filter system was maintaining temperature. Quotes were given for a tune up and a membership plan. Pics uploaded Made customer aware to change filter every 3 months or less
Changed out the thermostat out run system in cool and heat the system is running and operating like it should be. The face plate has one year from to day
The breaker is wrong need to have a 60 amp breaker for the indoor it has a 40 am on it right now homeowner is going to change it out under full part and labor warranty
Residential service call completed in Piedmont Alabama
Started up unit. Repaired short and low voltage circuit in air handler. System functions normally after start up.
Installed new system in Piedmont AL
Quote for new system in Piedmont Alabama.
Checked operation pan was full of water due to the drain line coming apart and was not draining. I raised the air handler up and reconnected the drain system is now operating properly at this time.