Replaced manual reset float switch with automatic reset float switch. Filter is new, inspected refrigerant level. 130/380 system is cooling. Operating pressures very similar to other unit just like this one. Cleared drain line.
Thermostat not working service call completed in Peachtree City Ga
Checked operations pan was full of water due to the coil freezing up and draining into pan. The filter was extremely dirty and was sucked into the furnace, it hasn’t been changed since January. Did not charge him because he said we did a maintenance not long ago and we did not change filters and he was not sure why. Also wants quote on quarterly maintenance
Checked operations furnace had a blown fuse checked system over and found shorted wires on ac. Fixed the short and replaced fuse. System is currently operating properly at this time.
Install a new basement system from the ground up.
Gave a quote for a new system.