Lithia SpringsGA30122 33.78-84.675
They kept us well informed of who was coming and when and their prices were fair. They fixed the problem and we have AC again.Lithia SpringsGA30122 33.76-84.6475
Lithia SpringsGA30122 33.7725-84.6625
Patrick went above and beyond what I expected, very satisfied with his work as well as his kind personality, very professional 5 starsLithia SpringsGA30122 33.79-84.6675
1 system pm renewal- Checked heating operations of system. Replaced filters, checked capacitor outputs and amp drawls, replaced fan belt, triggered safety switches, cleaned flame sensor, cleaned burners, and cleared drain line. system is operating properly at this time. 6-18x18x2, B51 belt, pics uploaded Sending invoice to email for payment
I performed a heating maintenance on a single gas furnace Ac unit I replaced the 16x25x1 filter I checked all electrical components and checked the temp rise and checked the heat exchangers and checked the gas pressures and adjusted the gas pressures and checked and cleaned the flame sensor everything is in good working order at this time.
Performed maintenance on both furnaces in the attic changed out both 16 x 25 by one filters checked capacitors cleaned off flame sensor and checked amperage on fan motor everything seem to be operating normal at this time
The drain line was clogged, so I unclog the drain line make sure that there was water draining out of the system and nothing could get stopped up again
Found low-voltage short just before furnace. White wires were not connected properly. Made necessary repair ensuring good connection. Furnace is now operating.
I performed a heating maintenance on a single heat pump air handler package unit I replaced the 16x25x1 filter I checked all electrical components and checked the Freon levels and cleaned the drain and cleaned the condenser everything is in good working order at this time.
Warranty maintenance call back Shortly after maintenance was performed drain line clogged with hair. During maintenance coil was treated with self rinsing evaporator cleaner/sanitizer and brushed. During today’s visit drain line was cleared and debris was vacuumed from evaporator pan underneath coil. Residual water was removed from return Plenum. Advised customer to allow another day or so for the rest of water to dry up before replacing ceiling tile.
Performed maintenance on two rooftop package units. Replaced all filters. Carrier unit uses four pieces 16 x 16 x 2 and has a aX 41 belt. Belt was tightened on this visit. Carrier unit is doing OK. The older York unit was frozen but I believe that was due to a dirty filter. York utilizes 20 x 22 x 2 filter and has no belt is direct drive. Instructed owner to turn that unit off overnight and leave the fan on to make sure it gets to the defrosted thoroughly. Customer is interested in having an estimate for maintenance program.
I replaced a double pull contactor and also changed a 16x25x1 filter system was shorted at the contactor system is running and operating like it should be
Performed inspection on air handler inside attic, treated drain line inside and checked temperature rise and also heat strip operations, changed 14 x 20 x 1 filter in ceiling grill, performed inspection on furnace inside crawlspace, treated drain line and change filter, checked pressure switches in tubes, cleaned igniter and sensor, did not change 16 x 25 x 1 filter at this time, checked refrigerant levels on heat pump, both systems are clean and operating normally at this time.