They kept us well informed of who was coming and when and their prices were fair. They fixed the problem and we have AC again.
Patrick went above and beyond what I expected, very satisfied with his work as well as his kind personality, very professional 5 stars
Txv has been changed and maintenance on both systems have been done. 20x20x5 Filter that was left off from last time was installed. Systems are now cooling properly
Install system Wednesday customer. Customers will be home at 3 to sign paperwork
System as bad TXV on Upstairs unit. System at first appeared to be low on refrigerant technician began to add die and refrigerant and noticed that the suction side wasnâ€™t going up at all while the head pressure was skyrocketing. System has adequate return airflow in the evaporator coil is clean along with the filter. Technician has ordered TXV somebody needs to reach out to the customer for scheduling. Returning technician needs to bring a 20 x 20 x 5 media filter for the upstairs system And rents the outdoor coils.
2 system ccm renewal- (heat- furnace and a heat pump) Main-Checked heating operations of system. Replaced filter, checked capacitor output and amp drawl, trigger safety switches, cleaned flame sensor, cleaned burners, and cleared drain line. system is operating properly at this time. 16x25x1 Upstairs- Checked operations of system. Replaced filter, check capacitor output and amp drawl, checked refrigerant levels and auxiliary heat, triggered safety switches and defrost mode, and cleared drain line. System is operating properly at this time. 16x20x1. Customer is interested in uv lights but wants to talk to wife first.
Diagnosing an A/C unit
Replaced outdoor fan motor