They kept us well informed of who was coming and when and their prices were fair. They fixed the problem and we have AC again.
Patrick went above and beyond what I expected, very satisfied with his work as well as his kind personality, very professional 5 stars
Performed inspection on air handler inside attic, treated drain line inside and checked temperature rise and also heat strip operations, changed 14 x 20 x 1 filter in ceiling grill, performed inspection on furnace inside crawlspace, treated drain line and change filter, checked pressure switches in tubes, cleaned igniter and sensor, did not change 16 x 25 x 1 filter at this time, checked refrigerant levels on heat pump, both systems are clean and operating normally at this time.
Performed heating inspection on air handler inside attic, change 16 x 20 by one filter and blew out drain line, checked blower motor amps and heat strip operations, performed inspection on furnace inside basement, treated drain line and chain 16 x 25 x 1 filter, checked temperature rise on both systems, checked blower motor and pressure switches and tubes, cleaned igniters on furnace downstairs, performed inspection on outdoor condensing units, checked refrigerant levels in all electrical components, both systems were clean and operating normally at this time.
I performed a heating maintenance on two heat pump air handler I replaced one 20x20x5 and one 16x20x5 filters I checked all electrical components and checked the temp rise and cleaned the drain line and I checked the Freon levels and checked the capacitors and cleaned the outside units everything is in good working order at this time.
I performed a heating maintenance a single gas furnace Ac unit I replaced the 20x20x1 filter I checked all electrical components and checked the gas pressures and checked the burners everything is in good working order at this time.
Commercial service call completed in Lithia Springs Ga
Thermostat is sending cooling signal at all times. Thermostat will need to be replaced. 2 heat 2 cool conventional. Installed new thermostat and tested system operation unit is cooling normally. Cleared condensate drain line on rooftop unit if water continues to drip from ceiling then it will not be related to the rooftop unit.
Residential Service Call completed in Lithia Springs Ga
I performed a service call on a single gas furnace Ac unit I replaced the 16x25x1 filter and I found that the condenser was very dirty and the dual capacitor was going bad I checked the Freon levels and I replaced the 35/5 mf capacitor and I cleaned the condenser by taking all the sides of and putting coil cleaner on and spraying it down .
Installed two furnace control boards on the main floor in the upstairs furnaces. Performed functionality check in both furnaces. Both furnaces operate normally after replacing the furnace control boards.
Found system running head pressure over 500 causing system to trip out on high pressure temporary disconnected high-pressure sensor system was running believe blockage is in refrigerant lines will get price for repair if parts are available