Will use again
Residential Service Call completed in Jonesboro Ga
Upstairs system has relatively new Goodman gas furnace. With older R22 Ac/outdoor unit and evaporator coil. The furnace was not wired properly resulting in low air speed. Today technician relocated the Y1 wires from thermostat and outdoor unit to proper location on furnace control board. Furnace now operates blower at proper speed for cooling. Outdoor unit at this time is operating normally and refrigerant level is OK system is cooling.
Maintenance/Tune Up completed in Jonesboro Ga
I performed a cooling maintenance on a single gas furnace Ac unit I replaced the 16x25x1 filter I checked all electrical components and checked the temp drop and cleaned the drain line and I checked the Freon levels and checked the capacitor everything is in good working order at this time.
Residential service call completed in Jonesboro Ga
Checked all operations and system operating normally.
Added 1 lb of R410a to cooling system
Jonesboro Ga - Filter change for customer.
Replaced two wire 24 V gas valve in furnace. Furnace is now operating properly. Also replaced batteries in thermostat.