Performed system maintenance. Replaced 14x20x1 filter, cleared drain line, and inspected refrigerant level. System is operating normally at this time.
Got to house and performed inspection on air handler in cellar, found bad capacitor and also a bad conensate pump, replace capacitor but unit still did not come on, Replace condensate pump as motor had failed, Turned the unit on and it is now running as it should at this time, inspected outdoor electrical components and refrigerant and everything looks good.
Maintenance/tune up completed in Forest Park Georgia
Maintenance/tune up completed in Forest Park Ga
I performed a cooling maintenance on a single gas furnace Ac unit I replaced the 20x25x1 filter I checked all electrical components and checked the temp drop and cleaned the drain line and I checked the Freon levels and checked the capacitor everything is in good working order at this time.
System leaking water service call completed in Forest Park Georgia
System leaking water because of a clogged drain. I made repairs and system is now cooling properly. 16x25x1 Sending invoice to email for payment
System needs replacement. Units are very old. Emailed estimates for replacement
Upon arrival, found common wire burnt off of the capacitor on the outside condensing unit. Found the capacitor Measured below specifications. Replaced the capacitor and found that the fan motor to the outdoor condensing unit was inoperative. Recommend replacement of the entire system at this time due to the age of the system and due to the efficiency of the system.
Checked system and system needs to be replaced. Units are very old.