Upon arrival, found the service disconnect plug not plugged in correctly at the outdoor unit due to tree work being done Close to the unit and the workers not plugging in the service disconnect correctly. The system functions normally after plugging the disconnect plug in correctly for the out side unit. The customer states there is an addition to the house that does not get good airflow. After discussing the situation with the customer, it is advised that a comfort specialist come and meet with a customer to explore options to install a mini split system for that particular room. Sent service an email explaining the customers wishes and we will be reaching out to the customer to schedule that appointment.
Installed universal furnace motor. Had to use wing mount kit. Also installed new 7.5 mf capacitor for motor. Upstairs system. Tested motor operations and inspected operations. Found filter inside plenum and removed it. System should only have 1 filter installed at a time.
Checked operations the generac box was preventing the system to power on I bypassed it and they are going to have it replaced. System is now working properly at this time. Brandon did not answer will need to send invoice.
Checked operations the drain was clogged, blew the drain out and cleaned the p trap. Ran water to issue it drained system is operating properly at this time.
Checked operations the furnaces blower motor is bad, will need a 115v 1075 universal motor to replace.
Cooling maintenance completed in Fayetteville Ga
Cooling maintenance completed in Fayetteville Ga.
Install of new system in Fayetteville Georgia.
Fayetteville Georgia - Quote for new system
Found leak at solder joint on outdoor unit. Pumped down system, repaired refrigerant leak, vacuumed system and properly charged system with R410a refrigerant. System operating properly.