Performed maintenance on air handler in attic changed 20 x 20 by one filter checked all electrical components for broken and loose connections checked amperage on fan motor check the voltage on his strips everything is running normal at this time
Found 35-year-old heat pump not working send estimate
Correct the heating for master bedroom and main foyer unit system is currently working at this time
Upstairs and basement systems were not heating because of dirty filters. I made corrections and systems are now working properly. 16x25x4, 20x20x1, 14x25x1. I did not have a 4” filter for the upstairs so I installed a temporary 1” filter until customer orders some. I made customer aware to change 1” filters every 3 months or less and 4” filter every 6 months or less. Pics uploaded
I performed a heating maintenance on two gas furnaces Ac units I replaced both 16x25x1 filters the one in the attic is a very old furnace I tried to get the burners to ignite but they are not working I did get the pilot to light but it was not coming on homeowner is aware of this and I recommended replacing the furnace he does not want to replace it at this time, the one in the basement I checked all electrical components and checked the temp rise and checked the heat exchangers and checked the gas pressures and checked the flame sensor everything is in good working order at this time only n the basement unit.
1 system CCM-Checked heating operations of system. Replaced filter, checked capacitor outputs and amp drawls, triggered safety switches, cleaned flame sensor, cleaned burners, and cleared drain line. system is operating properly at this time. 20x25x5 bring every visit. Pics uploaded
2 system pm 2nd visit-Checked heating operations of systems. Replaced filters, checked capacitor outputs and amp drawls, triggered safety switches, cleaned flame sensors,cleaned burners, and cleared drain line. systems are operating properly at this time. 2-16x25x1, pics uploaded, made him aware to change filters every 3 months
I performed a heating maintenance on a single heat pump air handler unit I replaced the 20x20x1 filter I checked all electrical components and checked the temp rise and checked the Freon levels and checked the capacitor it is working for now I highly recommend replacing the the unit do to the age of the unit and we do not use R22 Freon any more.
Completed one ccm maintenance on furnace located in basement I inspected exhaust and gas to ensure it was up to code, i changed one 16x25x4 filter customer provided, I cleared pressure tube and cleaned flame sensor I checked capacitor mfd as well as inducer motor and blower amps I watched furnace through 2 cycles, fired up brought home to temp. Once again made homeowner aware of age of system opted not to speak with comfort advisor yet but will before new year.
Completed one ccm maintenance on furnace unit located in crawlspace, i changed 1 20x25x5 filter I cleared pressure tube cleaned flame sensor, checked capacitor mfd as well as inducer motor and blower motor amps fired unit up and watched run through 2 cycles, brought whole home to temp.