Complete single system cooling maintenance. Replaced 16x25x1 filter,checked all electrical components on indoor unit, cleared and treated drain line. Cleaned outdoor unit coil, checked all electrical components and checked charge. System is currently cooling at manufacturers specifications.
Checked in and around furnace for any problems or future problems everything looked good changed filter and clean flame sensor
I performed a cooling maintenance on 8 heat pump air handler units I replaced 7 16x20x1 filters and 1 12x20x1 filter I checked all electrical components and cleaned the drain lines and checked the condensers 7 out of 8 units are in good working order except for one on building B the second unit on the right has an electrical issue but it’s with the unit there is something wrong with the wiring from the panel to the condenser.
I look at 6 systems and there is 3 systems running and cooling. there is one that is empty and leak at in door coil and another one that has a bad fan realY and there is a system that there is no power going to the unit from the disconnect change out condensation pump on one of them getting with Patrick to get pricing for coil and fan relay.
Commercial Service Call completed in Ellenwood Ga
Performance inspection on 11 air hand or units, all 11 air handler‘s are running and blower amps are good, changed one 16 x 20 x 1 filter and removed 10 20 x 22 x 1 filters but did not replace them as I didn’t have them, treated all drain lines, removed water out of one drain pan, performed inspection on all 11 heat pump units, out of 11 only three outdoor units are coming on and only two of them are staying running, found melted wiring on one unit, two units with low pressure shut off, two with low-voltage errors, and one with no power to the board, customer would not like to pay for repairs at this time but just for the maintenance itself, will need a tech back out to install all 10 20 x 22 x 1 filters. Also did not do maintenance on other two buildings, there is four units on one building and four on the other.
Thermostat service call in Ellenwood Georgia
Ellenwood Georgia - inspection/maintenance completed.
Performed inspection and maintenance on one attic furnace unit and one outdoor condensing unit. Filter size is 16 x 25 x 1. Replaced filter and treated drain line. Inspected blower motor amperage and overall cleanliness of the blower compartment. Inspected outdoor condensing fan motor amperage, capacitor, and Freon level. Washed outdoor condensing unit coil. The system is operating normally at this time and all measurements taken are within specifications. The customer has opted to sign up for the monthly membership program at this time.
Customer complained about a large puddle of water beside AC systems. I changed 2-16x25x1 filters, checked Freon levels and systems are working properly. Customer mentioned she hasn’t ran her ac since she’s moved in a month ago. I made her aware there’s possibly a water leak under ground or water heater valve is leaking.