Was able to schedule service on the same day. Dennis arrived promptly and quickly diagnosed and solved the problem. He explained what he was doing and firmly reattached the wall inlet to my air conditioner which had been loose. The price for the service was extremely fair..DunwoodyGA30338 33.925-84.3
Oh time, efficient, honestDunwoodyGA30346 33.92-84.34
Performed maintenance on all three systems. Replaced all three filters two pieces 16 x 20 x 1 and one 16 x 25 x 1. Cleared and treated condensate drain lines and pumps with chlorinated tablets. Inspected electrical connections and components as well as refrigerant levels. Cleaned outdoor condensing coils. Also replaced defrost control board for upstairs system outdoor unit. After replacing defrost control board, technician tested system operations and unit is now operating properly.
Replace upstairs Lennox air handler Evaporator coil under manufacture warranty until October 2023
Connected breaker for the upstairs Rheem AC that construction guys unplugged for they’re power tools. System is now working properly. 2-16x25x5, pics uploaded. Made customer aware to change the filters every week during construction. Customer also wants a quote on a humidifier for the main level system.
Performed inspection on furnace inside crawlspace, treated condensate pump and changed 20 x 25 x 4 filter, inspected all electrical components on furnace, performed inspection on outdoor condensing unit, checked refrigerant levels and all electrical components, the unit is clean and performing as it should of this time. Homeowner provided filter
Sent quotes for evaporator coil labor System is under part warranty until October 2023 Will be ordering from Lennox Lithia Springs in the morning
Sent quotes for upstairs evaporator coil
Upstairs 2018 Lennox heat pump low on refrigerant. Customer approved the BEST option with adding refrigerant, preforming a electric leak search to pinpoint leak and complete a tune up on both systems. I added 4lbs of refrigerant and found leak in evaporator coil in air handler. I will be calling supplier about part availability and warranty. In the meantime system is cooling. 2 system tune up- Checked operations of the air conditioning systems. Replaced filters, checked amp drawls and capacitor outputs, checked delta T, cleared drain lines, checked refrigerant levels and cleaned outdoor condensing coils. Systems are operating properly at this time. 16x25x4, 20x25x4. Pics uploaded Sending invoice to email for payment
Upstairs heat pump has bad defrost control board. Have board bypassed so that it will cool. Will be ordering board from Apex lithia springs. Not sure of price yet.
Replaced bad 45/5 mfd dual capacitor for upstairs a/c. Checked system operation and system operating properly.
The system is working and cooling the house like it should be the sub cooling and charge is where it needs to be the rental woman had the heat on when I got here Check out everything , the system is running and cooling fine.