System not cooling service call completed in Duluth Ga
Residential service call completed in Duluth Ga
Installed rebuild kit for main level system and unit is now cooling properly. 16x25x1. Compressor is also making weird noises and overheating. Customer is aware of systems age and wants to speak with a comfort advisor. She also mentioned that we have her house in Carrollton under 3 systems. She said it only has 2 systems. Pics uploaded
Upstairs 3 ton system drain line restricted not allowing water to flow out fast enough. Blew out drain line with CO2 cartridge and used vacuum to take care of residual. EchoNet thermostat displaying no current codes or any significant codes in history. System is cooling well however thermostat is located directly under attic stairs. Estimate will be provided to customer for attic tent. I would also recommend adding insulation to attic. Warranty no charge for drain line it is a maintenance item.
Maintenance/tune up completed in Duluth Ga
I performed a cooling maintenance on three gas furnaces I replaced all three 16x25x1 filters I checked all electrical components and checked the temp drop and I cleaned the drain lines and I checked the Freon levels and checked the capacitors everything is in good working order at this time.
Maintenance/Tune up completed in Duluth Ga
New 1 system pm-Checked operations of the air conditioning system. Replaced filter, checked amp drawls and capacitor outputs, cleared drain, checked refrigerant levels and cleaned outdoor condensing coil. System is operating properly at this time. 16x25x1 I also replaced the 10mfd capacitor for blower motor and repaired a leak and the indoor coil. Has a 1yr warranty on capacitor and leak repair Pics uploaded Not interested in replacement
Quote for RTU