Comfort Solutions installed and now maintains my AC unit and does an awesome job. I don’t have to worry about remembering to schedule as their Customer Service team is great about keeping me up to date on maintenance. Thanks everyone!DecaturGA30032 33.725-84.2675
Prompt, polite, knowledgeable- could not have been more satisfied.DecaturGA30030 33.77-84.285
Patrick was pleasant and completed the work quickly without any problems.DecaturGA30030 33.7925-84.295
1 system ccm- Checked heating operations of system. Replaced filter, checked capacitor outputs and amp drawls, triggered safety switches, cleaned flame sensor, cleaned burners, and cleared drain line. system is operating properly at this time. 20x25x1, pics uploaded
Customer received wrong model number thermostats that do not have any humidity control options. Technician did explain that with the current systems, over cooling is the only option for dehumidification without adding a stand alone type dehumidifier. Customer currently has multiple dehumidifiers throughout home. And temperature is around 80. Customer will contact office once he has received correct thermostats.
Warranty parts and labor. Replaced upstairs damper motor. Tested operations of the zoning and damper motors. All motors are opening and closing properly. $40 for previous invoice for filter was paid on January 27 and customer no longer has any outstanding balance.
Performed maintenance on down flow furnace in closet changed 24x24 by one filter cleaned off flame sensor checked all electrical components for broken or loose connections checked capacitor checked amperage for fan motor everything is running normal at this time
Warranty- installed p-trap for air handler in crawl space. Pics uploaded
Installed 1-16x25x5 media filter. Performed 1 system maintenance. One of the damper motors for upstairs is not operating properly, will need to replace. Full parts and labor.
Located horizontally in crawlspace with limited clearance
Converting gas system to an all electric heat pump system.
Warranty- tightened common wires for thermostat and main level rheem furnace is now working properly. Didn’t charge today because when we were out to reroute drain we must have forgot to tighten wires. Pics uploaded Customer is also interested in quotes on thermostat he sent to our email. Talk to Patrick
Performed maintenance on to air handler‘s and heat pumps Change 20 x 25 x 5 pop-up media filter checked all capacitors checked amperage on fan motors checked voltage on heat strips checked Freon levels everything was operating normal at this time