Comfort Solutions installed and now maintains my AC unit and does an awesome job. I don’t have to worry about remembering to schedule as their Customer Service team is great about keeping me up to date on maintenance. Thanks everyone!DecaturGA30032 33.725-84.2675
Prompt, polite, knowledgeable- could not have been more satisfied.DecaturGA30030 33.77-84.285
Patrick was pleasant and completed the work quickly without any problems.DecaturGA30030 33.7925-84.295
Completed- installed uv light in supply plenum and replaced furnace switch with a combination outlet switch for power to the uv light.
Could not install will need materials in emailed list
Completed single system cooling maintenance. I replaced 16x25x1 filter, checked all electrical components and cleared drain line. I checked all electrical components cleaned condenser coil and checked refrigerant charge on the outdoor unit. System is currently cooling at manufacturers specifications.
Warranty new construction Reconnected non-insulated, flexible ducting to bathroom exhaust fan, that had detached. Individual who I met on site informed me that they are renting.
Install 3 customer provided thermostats Complete. Installed three thermostat and tested functions.
Performed 1 system pma cooling maintenance replaced 1 customer provided 16x25x5 filter checked electr Components and refrigerant charge all systems operating properly at this time
Arrived and found unit running the blower but thermostat was blank. I confirmed function of the system and found thermostat was the issue. Thermostat does not have a common wire and the batteries were installed incorrectly causing the screen to be blank. I corrected batteries and adjusted wires in thermostat backing plate to avoid wires rubbing together. System is currently cooling and operating off of the thermostat.
Completed one ccm maintenance on two furnace ac and one air handler heat pump I changed all filters and checked thermostat operations, I treated drain lines triggered pan switches and checked all electrical connections. I checked overall cleanliness of units and blower amps , all clean at this time. I checked electrical components outside and checked pressures systems are clean and operating properly at this.
Completed two system cooling maintenance. I replaced 2-16x25x1 filter,cleared drain lines and checked all electrical components on the indoor units. I cleaned the coils,checked all electrical components and checked the refrigerant charge on the units. Units are currently cooled at manufacturers specifications.
Arrived and adjusted manual dampers previously installed that were set open. Customer will try this adjustments to see how they work. It was a mild temperature morning on visit. If we need to make further adjustments we will need to install more manual dampers to balance out the air flow better.