Replaced bad 3 pole contactor for rooftop Package unit.
1 system PM 2nd visit- Checked operations of the air conditioning system. Replaced 2-20x35x2 filters, checked amp drawls and capacitor outputs, checked delta T, cleared drain, checked refrigerant levels and cleaned outdoor condensing coil. System is operating properly at this time. Pics uploaded, roof access in the back
Installed blower motor for upstairs furnace. Full p and l.
Blower motor for upstairs furnace is bad. Module is running and then stopping then running again. Ordering motor from Apex.
Performed 2 system cooling maintenance. 1-16x25x5 media filter is brand new and 1-16x25x1 filter is brand new. Both systems clean and performing properly. Customer signed up for ACH to extend labor warranty for upstairs system.
Replaced bad t6 thermostat. Lost display. Warranty
I performed a maintenance on a single gas furnace Ac unit rooftop unit I checked all electrical components and checked the heat exchangers and checked the gas pressures and checked the capacitor and checked the flame sensor I checked the filters they are two 20x35x2 filters they will have to be ordered for the next visit everything is in good working order at this time.
Contractor said Air handler was leaking water upon inspecting units found two couplings on the drain PVC where the glue came undone glued both couplings everything should be operating normal at this time
Looked at job
Replace TXV but will need to come back to charge 5 ton unit I ran out of Freon