Warranty- System we installed March 8th, 2023 is working properly. I did inspect everything and only issue I found is that the installers did not turn off outdoor sensor on the T6 thermostat (AC is not equipped with one). 16x25x5, pics uploaded Is aware about warranties and memberships
Sound that was being heard in the back operational room was caused by heavy airflow. Technician located manual air volume damper, on ductwork and adjusted airflow down to reduce sound. Technician also made observation that the equipment does not appear to have had any maintenance since installation having original filters that come with the equipment. Technician highly recommends that all three systems be serviced thoroughly, including replacing filters and belt replacement and/or adjustments. Estimate for maintenance of the systems will be provided via email.
ZERO percent interest financing for 36 months WAC
Completed one system cooling maintenance. I replaced customer provided filter,cleared drain line and checked all electrical components on the indoor unit. Cleaned outdoor unit,checked charge and checked all electrical components. System is currently cooling at manufacturers specifications. Outdoor unit was extremely clogged with grass. I highly recommend either changing mowing directions or turning the thermostat mode to off while cutting the side yard.
ZERO percent financing for 36 months WAC
System was approprimately 3 pounds over charge recovered refrigerant and suction pressure was still high couldn’t find any obvious issues system is now cooling recommended ac upgrade due to weak compressor customer enrolled into maintenance program so no charge
ZERO percent interest financing WAP
Located horizontally in the attic with plenty of clearance
I performed a heating maintenance on a heat pump air handler I replaced the 16x20x5 filter homeowner supplied I checked all electrical components and checked the temp rise and checked the Freon levels and checked the capacitor everything is in good working order at this time.
Residential quote completed in Conyers Ga