John was really informative and helpful. He wasn’t in a rush but took his time and did a thorough inspection of our unit.College ParkGA30349 33.6125-84.58
I truly enjoyed the service that Patrick provided. He fixed the issue and found a remedy to prevent any further issues.College ParkGA30349 33.605-84.575
Excellent service, personable tech, will use again, will recommend to friends.College ParkGA30349 33.6325-84.52
Completed filter change only pics uploaded to ST, front office handled payment. Filters signed and dated pics uploaded to ST.
Performed inspection on air handler inside closet, blew out drain line and changed 20 x 20 x 1 filter, checked blower motor amps. Performed inspection on outdoor condensing unit, checked refrigerant and all electrical components. Rinse down unit in the unit is clean and performing as it should at this time. Filter size is not 16 x 20 x 1.
I performed a service call on a single gas furnace Ac unit I found that the hot surface igniter was bad and i replaced the igniter and the unit came on everything is in good working order at this time.
Removed and flipped media filter cabinet so that door will properly stay on. Reworked gas line and condensation drain line. Sealed up all air leaks and hung ducts that needed hanging. Checked operation and system operating properly. No charge
Need to return and remove return plenum and filter box and raise up and fix emergency pan. Filter box needs to flipped 180 degrees. Silicone between furnace and coil. Mastic supply plenum. Reinsulate indoor and out door armorflex. Rework drain line from coil. Check plug in emergency pan. Hang up 6” duct off back of supply plenum. Install proper sediment trap in gas line. See pictures.
Furnace power switch was turned off. Turned switch on and system operating properly. No charge
Completed one ccm maintenance on gas furnace located in walk in attic space i changed 1 14x25x1 filter I checked gas and exhaust to ensure they were up to code, they were. I cleared pressure tube, pulled flame sensor, checked capacitor mfds watched unit cycle the first time took my inducer motor amps and blower motor amps. All was within range, also checked outdoor electricals, capacitor mfd and fan motor amps, everything within range, informed homeowner of sheet rock dust inside unit from remodel, and age of unit although it is not causing any problems. System operating as it should at this time. Pics uploaded to ST.
Warranty parts and labor 2 T6 thermostats have failed. Blank screens and warm to the touch. 26 Volts present at both. Replaced both thermostats one in the master bedroom downstairs and one right at the top of the stairs, upstairs. I believe recent construction of new homes in the area may have caused a power fluctuation that resulted in the thermostats failing. After thermostats were replaced, both systems returned to operating normally.
Change 16 x 25 by one filter cleaned off flame sensor checked capacitor and checked for any loose wires or anything that may cause problems in the future everything look great
Change filters check capacitors clean flame sensors and checked in and around all 4 furnaces to make sure there were no problems Everything was perfect