John was really informative and helpful. He wasn’t in a rush but took his time and did a thorough inspection of our unit.
I truly enjoyed the service that Patrick provided. He fixed the issue and found a remedy to prevent any further issues.
Excellent service, personable tech, will use again, will recommend to friends.
On arrival HVAC system not operating at all. Found very dirty clogged filters one upstairs and one downstairs located in filter back return grills. Both filters are 14 x 20 x 1 size. Filters need to be replaced Filters need to be replaced every 90 days. found no high-voltage present at furnace in attic and traced back to electrical switch. Made high-voltage electrical repairs and replaced switch. Replaced both filters and performed AC tuneup. System is now cooling properly.
Installed new Rheem 2 ton 20 seer heat pump in place of a/c unit.
2 system maintenance - College Park Ga
Setting in thermostat for heating was set to use both heat pump and furnace. Changed settings in thermostat to heat pump heating only. Adjusted refrigerant levels. System operating properly
Came out tested both units in heat and AC clean drains replaced all air filters, checked coils and were clean at this time, Inspected all contactors and electrical tested all functions with all tests pass, units are ready for service no issues found.
Performed inspection and maintenance on one attic furnace unit, one basement furnace unit, and two outdoor condensing units. Both systems are operating normally at this time.
Install/replacement of existing AC system in College Park Georgia.