Checked refrigerant charge, airflow and temperature drop. System is operating properly. Recommended installing dehumidifier in crawl space. Customer said he will install a dehumidifier. Also recommend installing a uv light. Sent options for customer to review.
Added some refrigerant to system and replaced filter. Advised customer about extending his labor warranty. No charge
Customer stated that upstairs 2007 ICP AC is not maintaining temperature during the day. I checked the refrigerant levels, air flow, amp drawls, 14x20x1 filter is still clean, and system is draining. Thermostat is in the bathroom and return grille is on the other side of home. Made customer aware that system is aging but they could try a Wi-Fi thermostat with a sensor to place by return grille. Pics uploaded Customer would also like quotes to reroute existing 6” pipe for the hood vent and add a dryer vent. Sending invoice to email for payment
Relocated return vent for upstairs system. Installed 14x20x1 filter grill.
Need one 14 x 20 pitch bird pan. 1-14inch flat tap. 1-14” flex. 1- 14 x 20 filter grill. A bag of white stripes.
Installed new condensate removal pump. Under warranty parts and labor. Filled pump with water and tested for proper operation. Pump is operating normally removing water, then shutting off with no backflow. Some sound of the condensate pump operating is normal when it is actively removing water.
Bad furnace control board. Needs to be replaced.
Located in mechanical closet with limited clearance
Replaced customer's thermostat.
Warranty- replaced shorted disconnect for Heat pump and installed T6 which is configured for 2nd stage. Pics uploaded, 20x20x5 Customer gave check for remaining balance