Replaced condenser motor and checked operations system is now operating properly at this time
fan motor needs to be replaced, itâ€™s gone bad as well as the capacitor, both burnt up due to a loose wire.
Customer is considering replacement. Customer requested estimates on repairing and replacing both systems. Quotes have been emailed to customer.
Trying to get this old system working