Tech (Jordan) was knowledgeable, patient with my questions. He was great!CantonGA30115 34.1775-84.4475
I've been with them since their beginnings. It is a fantastic Company......efficient and friendly! Thanks.CantonGA30115 34.23-84.3475
Performed a leak search with soap bubbles at the outside gas meter connections. Did an electronic leak search with detector inside the house. No leaks found, only gas being used at the time was for the three lit gas lanterns.
Formed at maintenance on one furnace and one air handler Air handler in the attic: customer provided her own filters checked all electrical components for broken and loose connections checked amperage on fan motor check the voltage on his strips everything is running normal at this time Furnace in the basement: customer provided her own filters cleaned off flame sensor checked all electrical components for broken or loose connections checked capacitor checked amperage for fan motor everything is running normal at this time
I performed a maintenance on a heat pump in the attic I checked the low voltage and the blower motor.I also performed a maintenance on a gas furnace in the basement look over the low voltage and also checked the compaster on the system everything is operating like it should be at this time. I had to replace the thermostat for upstairs cause it had went blank under full parts and labor warranty.
Performed inspection and maintenance on two attic furnace units. Checked pressure switches, tubes, and orifices. Filters did not need to be changed at this time. Treated both drain lines. Checked flame sensors, igniters, and capacitors. Performed functionality check on both furnace units. Checked blower and exhaust fan amperages. Both units function normally at this time.
The motor for the upstairs was burnt out changed it out and made sure that it opened and closed like it should be and working properly. There is a year warranty on the damper motor for the upstairs.
Customer said over the weekend when temperatures dropped below zero furnaces were not working properly probably to frozen condensate lines came out today did a once over on everything and make sure everything was running like it should and everything is running normal at this time
Thermostat controlled a 90% furnace vinyl tubing was frozen outside over the cold weekend causing the pump to stop working and shutting down the system which caused the thermostat to turn off weather has warmed up ice thought out condensate pump started working in thermostat is not working like it should talked with homeowner on how to prevent it from happening in the future and everything is running perfect like it should
The 2 system in the attic are frozen in the line the basement system is running and operating and heating full parts and labor warranty
I performed a heating maintenance on two units one in the attic is a heat pump air handler I replaced the 20x25x5 filter I checked all electrical components and checked the temp rise and checked the Freon levels and checked the capacitor and the basement unit is a gas furnace Ac unit I replaced the 16x25x5 homeowner supplied I checked the temp rise and checked all electrical components and checked the gas pressures and checked the heat exchangers and checked and cleaned the flame sensor both units are in good working order at this time.
Replaced blower motor for carrier gas package system and unit is now working properly. Pics uploaded. Has a 1yr warranty on motor Sending invoice to email for payment