Customer reports system not cooling properly upon inspection found a dirty condenser coil and system was approximately 2 pounds low on refrigerant cleaned coil and added 2 pounds of refrigerant system is now operating properly
Installed new evaporator coil under full parts and labor warranty.
Warranty- 2020 Rheem heat pump low on Refrigerant. I preformed a electronic leak search and found leak in evaporator coil. System is still under Rheem manufacture parts warranty and customer signed up for the maintenance plan within 1yr of installing so labor warranty is extended. I will be calling supplier for availability. In the mean time 6.5lbs of refrigerant was added to get system cooling until repairs. 20x20x5, pics uploaded
Performed inspection on air handler unit inside attic, treated the drain line and change the filter, checked all electrical components inside air handler. Performed inspection on outdoor condensing unit, checked refrigerant and all electrical components, the unit is clean and running as it should’ve this time.
Re-supported ceiling tile in service desk area. Pics uploaded Sending invoice to email for payment
Thermostat bad, not sending low voltage to air handler. Will need new thermostat
Arrived to replace flame sensor, determined it was not flame sensor but bad control board causing furnace to short cycle, will order part in morning if front office could remind me estimate built in service titan unsure if Matt already charged diagnostic fee so if not 98 will still need to be charged and dependent on price of board 100 or so dollars will need to be added to estimate informed customer of this as well, will email office that information once board is ordered.
Diagnose bad flame sensor for Goodman Furnace
Warranty- installed grilles that was on site. We will need to return to install the rest for main and pool house. Gate code- 1170 Pics and materials uploaded, get with Kyle on what type of grilles
Performed inspection on air handler changed out 20 x 20 x 5 filter check voltage on heat strips checked amperage on fan motor and checked capacitor on heat pump outside everything seems to be operating normal at this time