Maintenance/tune up completed in Buford Ga
Performed inspection on air handler unit inside attic, treated the drain line and change the filter, checked all electrical components inside air handler. Performed inspection on outdoor condensing unit, checked refrigerant and all electrical components, the unit is clean and running as it should’ve this time.
Residential service call completed in Buford Georgia
Customer had had issues with main level damper staying open. I adjusted the flapper and downstairs zone is now working properly. 20x20x1