Being responsible for 68,000 sq. ft. campus we always have issues. Comfort Solutions always goes above and beyond to help us. My campus is a 24/7 operation so you can imagine the weird hours we call for help. Comfort Solutions always make a bad situation good for us.BowdonGA30108 33.5575-85.2375
Upon arrival, outdoor fan not operating. After further evaluation the 1985 model system is past due for a upgrade. Will be emailing estimate for replacement.
Had small Freon leak at filter dryer. Fix leak at filter, dryer pressure checked and vacuumed.
Added 4 manual dampers and shut him down a quarter turn. Two push more air into the master bedroom.
Performed 1 system pma cooling maintenance replaced 16x25x1che Jed electrical components and refrigerant charge
Customer had concerns regarding the amount of condensation inspected all operations of system to find a slightly low suction pressure inspected the air filter to find it clogged replaced 16x20x5 customer provided filter and watched suction pressure return to required range system is operating properly
Add return vent in master bedroom to get air flowing better. Photos uploaded.
Arrived and diagnosed bad capacitor for the outdoor unit. Capacitor was only reading 2 mfd for the compressor out of 45 mfd required. I replaced capacitor and system is cooling. The house is 87 degrees so we have a high low side pressure at the moment but charge is correct. Jr approved repairs.
Change filters. Clean drain. Add a drawing tablet. Checked all e electrical components Clean outside condenser. Unit performance as it should.
Found unit not pulling in the condenser Contactor. System was in a high pressure lock out. Diagnosed bad capacitor for the condenser fan motor. Replaced capacitor and tested system. System is currently running and cooling the class room.
Need a supply or return in master bedroom. Talk to Jason about floorplan and what to do.