THE GENTLEMAN THAT CAME OUT WAS GREAT THE LADY IN FRONT WAS GREAT CANNOT SAY ENOUGH GOOD ABOUT THIS CO AND EMPLOYEESAustellGA30106 33.845-84.6225
Arrived in time. Handled the issue and was very courteous.AustellGA30106 33.8475-84.6125
the tech was great I am very happy with this companyAustellGA30106 33.845-84.6225
Performed maintenance on commercial package unit checked filters 2 16x25x2 they were still good changed in October cleaned off flame sensor checked capacitors checked amperage to fan motor everything is operating normal at this time
Furnace has bad gas valve. Couldn’t get in touch with owner. Gas valve is available at Carrollton Winair
Started up 2011 airflow furnace for right side duplex and system is now heating. I did make customer aware how extremely dirty the blower, blower assembly and controls are from never installing a filter. She will be thinking about cleaning. Pics and quotes uploaded. Sending invoice to email for payment
Tenant turning furnace on and off using breaker. Anytime power is on cooling operates. Years and years dirt and dust I have accumulated throughout the furnace as if no filter has been present. There is not a proper filter rack anywhere. It appears filters have been attempted to and stuck underneath the furnace however that has not been sufficient. Thermostat is blank. Replaced thermostat batteries and cleaned terminals. Thermostat is now working. There is no gas to the rightside apartment labeled A. On the side of the building there is a meter for apartment B on the left but no meter for apartment A on the right. A meter must be said and gas must be present for furnace to operate. I am not sure how long it’s been since the furnace has operated in heat mode and it is very likely to be quite unpleasant when it does operate from the accumulation of dust and debris over the years. Our office will schedule a return visit to operate furnace after gas is turned on.
Completed one ccm maintenance on furnace located in basement I did not change filter as it did not need to be at this time one was left with home owner, I cleared pressure tube cleaned flame sensor I checked inducer motor amps and blower motor amps as well as overall cleanliness of unit, everything was running as it should watched unit cycle 3 times.
Completed one ccm maintenance maintenance on furnace located in attic unit was DOA would not start at all, customer wanted to speak with comfort advisor
Completed two ccm maintenance on two gas furnaces located in attic and basement I did not change filters I checked gas and exhaust to ensure they were safe to operate, checked thermostats I cleaned flame sensors cleared pressure tubes fired units up checked inducer motor amps and blower motor amps informed homeowner of dust in basement unit due to construction of finishing basement, installed new registers and one supply pictures uploaded.
Performed 1 system heat pump tuneup. Replaced customer provided 20x20x5 media filter. Checked components and refrigerant pressures. System is clean and running properly.
Shutoff switch for furnace shorted. Customer did have a extra switch from the basement construction so labor was only charged. I also installed a 16x25x5 filter Pics uploaded
Fan side of capacitor had gone bad. Replaced with a new 50/5 cap and system started up.