Chris did a good job and identified that the wiring was incorrect and rectified the problem.
Everything went well, it was a good experience and most of all, prompt service.
He come to do scheduled biannual inspection. Texted us about 20 minutes before arrival to confirm appointment. Checked heat pump for both heating and cooling performance, replaced filters, inspected AC units and cleaned them. Very pleasant and professional.
Quick response no long wait friendly tech
Whenever we call, Comfort Solutions comes fast (within a day). The technicians are very nice. Happy to have them service our units, we have a yearly maintenance contract with them.
Inspected malfunctioning unit and found dampers were wired backwards. Repaired the wiring and tested.
Inspected a dual HVAC system. Checked operations both systems and found filters were dirty. Replaced filters. Checked a/c charges and had to add Freon to downstairs system as it was not charged properly. Both systems are currently operating properly at this time.
Completed second maintenance visit systems are operating properly at this time.
Gas valve for the range was leaking turned the valve off and tightened the cap it is no longer leaking gas.
Replaced HVAC filters and inspected system. Heatpump coils are clean. Compressor, fan, and capacitor draws read normal. System works in heat and the refrigerant charge is acceptable. Customer is currently satisfied and systems are running properly.
Completed second visit maintenance checked operations system is operating properly at this time.
Checked heating operations of systems. Replaced filters, checked capacitor outputs and amp drawls, trigger safety switches, cleaned flame sensors, cleaned burners, and cleared drain lines. systems are operating properly at this time. 2-16x25x1 Main unit was not cooling properly because of low Freon charge. Customer approved the Freon and unit is now cooling properly. Blower capacitor for the main unit was not in range and customer also approved to change part as well Suggested a quote on systems but customer is thinking about selling home so he is not interested in new systems or renewal of the maintenance at the moment
Checked for gas leaks and turned heat on all systems. Water heater was already lit upon my arrival
1 system ccm renewal- Checked heating operations of system. Replaced filter, checked capacitor output and amp drawl, trigger safety switches, cleaned flame sensor, cleaned burners, and cleared drain line. system is operating properly at this time. 12x25x1
Technician performed two full system heating maintenance which includes indoor furnace. Technician checked all electrical components for amp draw, mfd, and all high and low voltage connections. Technician checked blower wheel and exhaust fan. All pressure and safety switches were checked and tested. Filter was changed and dated for home owner. Technician removed and cleaned burner track and sanded ignition stick. Heat exchangers were surveyed and no cracks were found. Over all condition of furnace is in manufacturing specifications and safety codes.