Chris did a good job and identified that the wiring was incorrect and rectified the problem.
Everything went well, it was a good experience and most of all, prompt service.
He come to do scheduled biannual inspection. Texted us about 20 minutes before arrival to confirm appointment. Checked heat pump for both heating and cooling performance, replaced filters, inspected AC units and cleaned them. Very pleasant and professional.
Quick response no long wait friendly tech
Whenever we call, Comfort Solutions comes fast (within a day). The technicians are very nice. Happy to have them service our units, we have a yearly maintenance contract with them.
Upon arrival, found thermostat blink. Found 24 V coming from the transformer through the fuse. Found 24 V at the power wire coming from the board, but no 24 V at the thermostat wire that is connected to a float switch for the drain lines. Found water in the drain line with a float switch which indicated that the drain line was clogged. I flushed the drain line out and added to treatment tablets. I verified that the drain flowed freely after flushing. I advise the customer to use bleach water in the drain during each filter changed to try to keep the drain line from clogging again. Today’s visit will incur a charge of $128 to clear the drain line.
System not keeping up during the day because of a dirty filter and clogged drain. I made repairs and system is now cooling properly. 16x25x1 Made tenant aware to change filter every 2 months Sending invoice to email for
System has pinhole size leak on copper tubing inside the 2016 rheem outdoor heat pump. System has no refrigerant (410a). Luke is not answering so we will need to get approval before preforming repairs. Quotes and pics uploaded Reimburse diagnostic with repairs
Perform inspection on two furnace unit one in the basement one in the attic, change the filter in the basement, treated both drain lines and checked blower motor amps. Checked humidifier filter and components, Performed inspection on outdoor condensing units, checked all electrical components and refrigerant. Washed down outdoor units. Both the units are performing as they should at this time.
Performed inspection on two furnish units both inside the attic separate entrances, treated the drain line and changed the fiter, Checked all electrical components inside furnaces, performed inspection on outdoor condensing unit checked refrigerant and all electrical components on both systems, rinsed down both systems. Both systems are performing as they should at this time.
Replenished Freon until system can be replaced. Spoke with Dianne and she got it approved to add Freon now and to schedule a quote to replace the system.
System not cooling service call completed in Atlanta Ga
Residential Service Call completed in Atlanta Ga
#2 Ruud system not working properly because of a bad control board. Need 32ft ladder every visit Will be ordering board from apex lithia and work up a price with Brandon
Performed inspection on furnace inside attic, treated the drain line and change the filter, checked blower motor amps and capacitor. Performed inspection on outdoor condensing unit, checked refrigerant and all electrical components, cleaned outdoor unit. The unit is performing as it should at this time.
Few places in the Continental United States have the same random weather patterns as we do here in the Heart of Atlanta. You’ve probably heard the saying, “if you don’t like the weather in Atlanta, wait five minutes.” Well as true (and maybe sad) as that is, imagine the toll that the extreme weather can take on your home or business Heating and Cooling system! The crew from Comfort Solutions Heating and Cooling, LLC. have seen a lot of beat-up HVAC units in the Greater Atlanta area over the years. We know full well what the constant extremes in temperature can do to your system. Whatever you’re dealing with, we’ve seen it all. Our professionals know whether it’s more cost-effective to keep repairing your system, or if it will grant you much better return on your investment to replace your HVAC. We will never try to sell you something that you don’t need. That’s the Comfort Solutions Guarantee!
In addition to having access to some of the best HVAC financing on the market for new, sophisticated HVAC systems, Comfort Solutions now offers a perfect solution to keep your complex climate control system working at peak condition: the Comfort Club Membership. There are a lot of things in life that are beyond our control, that’s why there’s nothing else quite like being able to control the weather in your home or business, year round, with a Comfort Club Membership from Comfort Solutions.
For as little as $13/month, your Comfort Club Membership comes with:
Interested in a Comfort Club Membership, Total HVAC Replacement (for as little as $64 a month with approved financing), or any of the other award-winning services offered by Comfort Solutions? Contact our professionals today, and get a FREE on-site assessment for all your HVAC needs!