Great customer service, prompt & professional services were provided.
Maintenance/tune up completed in Alpharetta Ga
Maintenance/tune up completed in Alpharetta Georgia
Replaced all the filters, treated all drain lines, checked blower motor amps and caps, blower motor cap in back office space is reading 11 and it’s a 15 UF cap, recommend replacing soon. Also checked Delta T on units. All units are performing as they should at this time. Checked outdoor refrigerant levels and capacitors.
I performed a cooling maintenance on two gas furnace Ac units I did not replace the the 16x25x5 filters at this time homeowner said he will replace the in a few months I checked all electrical components and cleaned the drain lines and I checked the temp drop on both units and I checked the Freon levels and checked the capacitors on both units everything is in good working order at this time.
Quote for new system in Alpharetta Georgia
Service call completed in Alpharetta Ga
Emailed service video of locked rotor amps and unit tag.
Residential service call completed in Alpharetta Ga
Blew out vinyl tubing for condensation pump
Quote for new system in Alpharetta Ga