Great customer service, prompt & professional services were provided.
Performed full inspection on furnace and coil inside attic, changed 16 x 25 by one filter and clear drain line, checked blower motor amps and capacitor and all electrical components and connections inside furnace, triggered safety switches, removed and cleaned burners rack and send it igniter, checked pressure tubing and switches, performed inspection on outdoor condensing unit, checked refrigerant levels and all electrical components and connections, the system is clean and operating normally at this time. performed condensing wash on outdoor system.
Re-leveled pad for AC we just installed (no charge), I added 2.5lbs of 407c to upstairs system and I installed a customer provided regulator for cooktop Pics uploaded
Performed inspection on furnace inside attic, did not change 16 x 25 x 5 filter at this time, Treated and blew out drain line, checked blower motor amps, customer stated that he cannot run the system with fan only so I change the fan wire over on the board and it is now fixed, performed inspection on outdoor condensing unit, checked refrigerant levels and all electrical components, could not wash outdoor system due to leak inside wall.
Installed the txv pulled a bank and stared the system up .I made sure the system was charged and where it needs to be system is cooling and operating like it should under parts and labor warranty
Completed cooling inspection form for system #4 with thermostat located in back rear hallway office. Furnace and evaporator coil are 2002 year model Trane. Outdoor condensing unit is 2018 Rheem.
Inspection of unit number three. Thermostat located in first office to the left. System operating for row of offices.
Cooling/equipment inspection number 2 system number two
I performed a cooling maintenance on three units tow are gas furnaces Ac units and one is a heat pump air handler I replaced three 16x25x1 and one 18x20x1 filters I found that the main level unit is an R22 unit and it is out of Freon I recommend replacing the Ac unit the basement unit I checked all electrical components I found on that one the the condensate pump was not working and the pan switch was not working ether the pan was full of water I vacuumed all the water out and replaced the condensate pump I cleaned the drain line and checked the temp drop and the upstairs unit I checked all electrical components and checked the temp drop and cleaned the drain line and I checked the Freon levels and checked the the capacitors.
I performed a cooling maintenance on two gas furnaces Ac units I replaced one 16x25x1 filter and one April air 413 filter I checked all electrical components and checked the temp drops on both units and I cleaned both drain lines and I checked the Freon levels and checked the capacitors everything is in good working order at this time.
The faceplate went bad change it out and the system came on and is cooling full part and labor warranty