Great customer service, prompt & professional services were provided.AlpharettaGA30004 34.1275-84.2625
Great Service!!!AlpharettaGA30004 34.105-84.2475
Performed inspection on furnace inside attic, did not change 16 x 25 x 5 filter at this time, Treated and blew out drain line, checked blower and all the low voltage.
Completed 2 system ccm maintenance on 2 gas furnaces in attic i checked thermostat operations i inspected gas and exhaust i changed 1 16x25x1 filter, i did not change April aire filter it was good customer advised he’d order some off of Amazon, i pulled and cleaned flame sensor I cleared pressure tube. I checked capacitor mfd. I checked overall cleanliness of systems weather king was very dusty due to its age, i also checked blower. I watched units cycle getting inducer amps and blower amps. Systems running good customer wanted quote on weather king info emailed in , pics uploaded to ST.
Performed inspection and maintenance of two upstairs furnace Blower the flame sensors and igniters are clean, and both furnaces ignite and burn cleanly. Pressure switch tubes are clean.
Replaced Control board on the upstairs system they have one year warranty as of to day on the board. System is running and operating like it should be.
Lit both hanging heaters replaced one thermostat Honeywell T6 Sold two system maintenance agreement
Performed 2 system heating maintenance. Replaced filter for upstairs and apartment system. Main floor and master bedroom system filter still in good condition. Both systems are zoned, all zoning equipment operating properly.
Checked master bedroom system. Checked blower wheel and motor to make sure didn’t have any debris inside that would cause vibration but everything was clear. Checked vents in master bedroom and didn’t really notice anything out of the ordinary, did open up return vent veins thinking maybe it’s vibrating sometimes but didn’t find any issues with system operation or vents rattling or whistling. No charge
Master bedroom furnace
Performed maintenance on furnace cleaned off heat sensor changed out 14 x 25 by one filter checked amperage on fan motor also install disconnect box outside
Performed maintenance on furnace in Crawlspace changed out 16 x 25 by one filter cleaned off flame sensor checked capacitor checked amperage on fan motor everything seems to be operating normal at this time